Lapp multi-std. sc 2.2 1x4 brun r100
Multi-Standard SC 2.2 wiring cables are UL, CSA and HAR (VDE)* approved and are designed for use for control cabinet wiring as well as for installation in protective tubes, applicable within the scope of the UL- or Canadian or European standard specifications. They are especially qualified for wiring in industrial machines in accordance with NFPA 79.
HAR: Wiring cable for internal wiring acc. to EN 50565-2 (VDE 0298-565-2)
UL (AWM): oil resistant wiring cable for internal wiring
UL (MTW): acc. to ANSI/NFPA 70 (National Electrical Code)
CSA (TEW): oil resistant wiring cable for internal wiring of devices
H07V2-K ?HAR? (*) acc. to DIN EN 50525-2-31 resp. VDE 0285-525-2-31
UL (AWM) acc. to UL 758, Style 10269
UL (MTW) acc. to UL 1063, File-No. E198296
CSA (TEW) acc. to C22.2 No. 127-15
*For the dimensions 0.5; 0.75; 1.0; 16; 50; 70; 95; 120 mm² as well for the colours GN, YE and multi-coloured cores (except for GN YE) there are no HAR-approval available (X07V2-K)!
Conductor: fine-wired core of tinned copper strands acc. to IEC 60228 resp. VDE 0295, Class 5
Insulation: special PVC based compound
Electrical properties at 20°C
HAR H07V2-K U0/U: 450 / 750 V AV
UL (MTW)/CSA (TEW) U: 600 V
UL (AWM) U: 1000 V
Test voltage: 2500 V AC
Minimum bending radius
fixed installation: OD=8 mm: 4 x OD** / 2 x OD***
8<OD=12 mm: 5 x OD** / 3 x OD***
OD>12 mm: 6 x OD** / 4 x OD***
** at conventional usage; *** at cautious bending
HAR, (UL) MTW: -40 °C up to +90 °C max. conductor temp.
UL (AWM): -40 °C up to +105 °C max. conductor temp.
CSA (TEW): up to +105 °C max. conductor temp
HAR: IEC 60332-1-2 resp. VDE 0482-332-1-2
UL/CSA: 60°C oil rating
Tests: acc. to IEC 60811 resp. VDE 0473 and VDE 0472, UL 1581, UL 1063 and CSA C22.2
General requirements: These cables are conform to the EU-Directive 2014/35/EU (Low Voltage Directive)